[Date Prev][Date Next][Thread Prev][Thread Next][Date Index][Thread Index]
GBlist: Variable speed drives
I am trying to learn about the best way to vary substantially the ventilation
air flow in a current project. It is possible that the central ventilation
system ( which includes enthalpic recovery and deep dehumidification, which is
why it is central and not distributed) will need to vary output from 9000 cfm
down to as low as 1500-2000 cfm.
1) Is this too much of a turn-down ratio to expect from a fan and still be
2) How does the efficiency of variable speed drives vary with such a high
3) Does anyone have a manufacturer of VSDs who they particularly like?
This greenbuilding dialogue is sponsored by Oikos (www.oikos.com)
and Environmental Building News (www.ebuild.com). For instructions
send e-mail to email@example.com.