[Date Prev][Date Next][Thread Prev][Thread Next][Date Index][Thread Index]
Re: GBlist: Variable speed drives
In a message dated 97-04-18 15:25:18 EDT,
Marc.J.Rosenbaum@valley.net (Marc J. Rosenbaum) writes:
> I am trying to learn about the best way to vary substantially the
> air flow in a current project. It is possible that the central ventilation
> system ( which includes enthalpic recovery and deep dehumidification, which
> is why it is central and not distributed) will need to vary output from
> cfm down to as low as 1500-2000 cfm.
The complexity depends on the size and type of AC motor. My blower door
units have a 3/4 hp AC PSC (permanent split capacitor) motor like the kind
find on heat pump fans, and this type of motor can be controlled by an
inexpense (<$100) triac type speed control, like the ones you find in the
hardware store for overhead fan control. I use a 15 amp unit for my fans,
and this type control works
fine from 0 rpm to max rpm. The manual triac controls are available from
catalogs like WW Grainger (up to 10 amps) , and I have found a way to modify
this type of control so that it can be controlled from a PC Windows program.
I notice that Dwyer has a low cost ($69) electronic fan speed control
that works with 0-10 vdc input and controls AC motors up to 10 amps. See
part number FC-1000. I have not actually seen it.
I hope this is helpful. Are you in VA? The infiltec factory is in
Infiltec Air Leakage Control
This greenbuilding dialogue is sponsored by Oikos (www.oikos.com)
and Environmental Building News (www.ebuild.com). For instructions
send e-mail to email@example.com.